Can screw air compressor be placed directly in the open air environment?
Is that air compressor cover necessary?
We often encounter these problems when we go to customer sites. So today I want to talk with you about whether it is necessary to build an air compressor room, and what are the design specifications and precautions of the air compressor room?
According to the actual situation, the air compressor cover must have some, (and many users increase the sound insulation cover of the air compressor because of the influence of the sound of the air compressor).
If the conditions permit, it is necessary to build the air compressor room. But not as long as the construction of the air pressure room can be good, the design specifications of the air pressure room are also very particular.
For example: the heat dissipation of the air compressor room is not good in summer, and the high temperature of the air compressor frequently occurs. The design of the air compressor room is not standard, the maintenance of the air compressor is very inconvenient, and the construction of the waste heat recovery engineer of the air compressor is not convenient. Therefore, we should ensure that the home design of the air compressor in the air compressor room is reasonable.
If you are an air compressor engineer, what will you remind your users to pay attention to when designing the air compressor room?
- Before the design of the air pressure room, it is necessary to understand the design specifications and precautions of the air pressure room.
- Choose a place with low relative humidity, less dust, clean air and good ventilation. If the ambient temperature is too high (greater than 45 ° C), you are advised to take cooling measures, such as avoiding direct sunlight and opening doors and Windows, to avoid unnecessary high-temperature shutdown. If the ambient temperature is low (less than 0 ° C), the freezing point temperature of the lubricating oil must be controlled above the ambient temperature. Think about cold temperatures not only in the summer, but also in the winter, and think long term.
- If the factory environment is poor and dusty, a ventilation duct should be installed to guide the intake end to a place with clean air. The installation of the conduit must be easy to disassemble and install for maintenance, and the installation size refers to the external size of the air compressor.
- The space around the air compressor must be reserved enough for the entry and exit of other parts, and the distance between the air compressor and the wall must be more than 1500mm at least. It is better to have lifting equipment. The distance between the air compressor and the top space is more than 1500mm.
In short, the design of the air compressor room should be from the gas demand you want to meet, and not strictly in accordance with the book knowledge. But the basic precautions we should understand and master, and apply to the actual design of the air compressor room.
For more information about air compressors, remember to follow Kotech.
we offer a wide selection of high-quality air compressor packages in attractive prices, complete after sales, services with spare parts delivery within round a clock.